Case Study - Grain Handling
Updated: Aug 3, 2019
A grain processing facility had technical issues with a 6 pulse valve, 22kW motor reverse pulse jet cleaning system. High magnehelic gauge readings lead to maintenance staff reducing the pulse offtime in an effort to clean the bags but had resulted in a further deterioration of bag house performance.
PTronik System Supplied
PTronik supplied our pMC control solution which had the following features;
Header tank pressure sensor installed to monitor header tank pressure
On demand dP differential based controller instead of sequential timer (controller only pulses when the dust loading on the filter bags increases)
Supplied with tube cleaning purge system to ensure dP measurement accuracy
Remote access to controller settings and recorded data for remote analysis and diagnostics
PTronik used our pMC data logging controller and header pressure sensor to evaluate the current performance. Initial testing revealed the current sequential timer was pulsing faster than the header tank could recharge. This meant the pulsing discharge was very weak and had allowed the dP over the filter bags to reach an alarm condition and blind the bags.
The solution involved increasing the off time pulse duration to a point that allowed header tank recharging and setting the bag house to pulse under differential pressure control to prevent these issues from reoccurring in the future. Recording the bag house performance data and providing remote access allowed for long term verification of performance.
Field test data showed the PTronik pMC controller reduced the number of bag cleaning pulses by 29% to 64% depending on dust loading. This directly translated to;
Reduced air consumption
Increased filter bag life
Increased life of pilot and diaphragm valves
Operating the dust collector within the original design parameters
If PTronik can assist with your bag house performance issues then please get in contact email@example.com